System: STANDING FLOOR DESICCANT ROTOR DEHUMIDIFIER
Dehumidifier Type D-1500 berkapasitas 10 Kg/Hour pada suhu 20ºC dan 60% RH dengan Air Flow 1500 CMH.
Untuk pemesanan dan info lebih lanjut hubungi kami pada kolom Contact Us.
PT Inotek Pratama.
|Maximum Power||14.70 kW|
|Heater Current||50/25 A|
|Product Dimension||845 X 620 X 1180 mm|
|Net Weight||115 KG|
|Air Flow||1500 Cmh|
|The unit does not function||• Check that the fuse in the plug is ok.
• Check the plug is inserted in mains and mains power is on.
• Is tank full light on? Check water tank and empty if necessary.
• Check if the float of the water tank is blocked by foreign material. Is the float of water tank correctly positioned?
• Is the unit standing upright and level?
|Abnormal noises from the
|• Check and clean the air filter
• Is the unit standing upright and on a level surface?
|The unit leaks water||• Has the unit been tipped?
• Check if the float of the water tank is blocked by foreign material.
|Changes in temperature at the air outlet||• Is the unit on “Standby” or “Normal” operation status?
• The internal heater of the appliance will be switched on/off automatically.
|After the unit has been switched off, the fan motor is still running||• After the unit stops, about two minutes are needed to cool down the electric heater by running the internal fan.|
|The water tank was not properly inserted into the unit||• Make sure to insert the water tank in its right position.
• Is the float of the water tank correctly positioned?